Single slot CPU. 512 inputs and outputs (any mix). Up to 8K analog I/O. 0.4 microseconds per boolean function. 12 MHz, 80C186 microprocessor. Supports IC660/IC661) and IC697 I/O products Programmed by MS-DOS or Windows based software products running on Windows 95 or Windows NT over Ethernet TCP/IP or through the SNP port. 32 Kbyte battery-backed CMOS memory (fixed size). Configurable data and program memory. Battery-backed calendar clock. Three position operation mode switch. Password controlled access. Three status LEDs. Software configuration (No DIP switches or jumpers to set). Reference information inside front door. Functions The CPU 731 is a single slot PLC CPU which resides in an IC697CHS PLC rack. The CPU 731 is programmed and configured by MS-DOS or Windows based programming software to perform real time control of machines, processes and material handling systems. The CPU 731 communicates with I/O and smart option modules over the rack mounted backplane (IC697CHS750, 782, 783, 790, 791) by way of the VME C.1 Standard format. Supported option modules include IC697 LAN Interface modules, several Coprocessor modules, Bus Controller for IC660/661 I/O products, Communications modules, I/O Link Interface, and all of the IC697 family of discrete and analog I/O modules. Module operation may be controlled by the three position switch or remotely by an attached programmer and programming software. CPU status is indicated by three green LEDs on the front of the module. CPU 731 MODULE OK RUN OUTPUTS ON = OK, ENABLED MODULE IC697CPU731 LABEL 44A726758 101 MODULE FUNCTION 12MHZ CENTRAL PROCESSING UNIT BATTERY CONNECTIONS SERIAL PORT RS 422 COMPATIBLE INSTALL NEW BATTERY BEFORE UNPLUGGING OLD BATTERY. USE IC697ACC701 ENABLED USE THIS MODULE IN SLOT 1 ONLY RUN WITH OUTPUTS ENABLED RUN WITH OUTPUTS DISABLED STOP OK RUN ENABLED CENTRAL PROCESSING UNIT MS-DOS, Windows, Windows 95, and Windows NT are registered trademarks of Microsoft Corporation. GFK-0159J 12 MHz, 32 Kbyte Central Processing Unit 2 PLC CPUs August 1997 Series 90 -70 Programmable Controller Data Sheet Manual GFK-0600F 12-2 a42 RACK 7 BRM GBC BRM ONE METER ONE METER IC66* I/O BUS (7500 FEET MAXIMUM) PS I/O TERMINATOR (LAST RACK) TOTAL LENGTH OF ALL INTERCONNECTING CABLES FROM BTM TO LAST BRM IS 50 FEET (MAXIMUM). ALL RACKS MUST BE AT SAME GROUND POTENTIAL (8 RACKS MAXIMUM). NOTE LEGEND CPU SELECTED CPU MODEL BRM BUS RECEIVER MODEL, BEM711 BTM BUS TRANSMITTER MODEL, BEM713 GBC/NBC BUS CONTROLLER, BEM73* PCM PROGRAMMABLE COPROCESSOR MODULE, PCM711 PS POWER SUPPLY, PWR710/711/724/748 PARALLEL or NB C or N B C Figure 1. Typical PLC System Configuration Installation It is the responsibility of the OEM, system integrator, or end user to properly install the PLC equipment for safe and reliable operation. Product manuals provide detailed information about installation, startup, and proper use of the PLC equipment. The installation manual, shipped with your PLC programming software, describes how to properly install the equipment. If the PLC installation must comply with supported standards, such as FCC or CE Directives, please refer to the Installation Requirements for Conformance to Standards, shipped with the PLC programming software, for additional guidelines. Be sure that power to the PLC is turned off before installing the CPU 731 module Connect the battery to either of the battery connectors on the module (see Figure 2). Put toggle switch in the STOP position. Install in slot 1 of rack 0. (See Figure 1) Turn on power. The module should power up and blink the top LED. When the diagnostics have completed successfully, the top LED stays on and the second and third LEDs are off. The CPU is now ready to be programmed After the program has been verified the toggle switch may be moved to the appropriate operation mode position. The LEDs indicate the position of the toggle switch, memory protection status, and the state of the program. a42751g CURRENTLY INSTALLED CONNECTOR OPEN REPLACEMENT BATTERY CONNECTOR CPU 731 CPU 731 MODULE OK RUN OUTPUTS ON = OK, ENABLED MODULE IC697CPU731 LABEL 44A726758 101 MODULE FUNCTION 12MHZ CENTRAL PROCESSING UNIT BATTERY CONNECTIONS SERIAL PORT RS 422 COMPATIBLE INSTALL NEW BATTERY BEFORE UNPLUGGING OLD BATTERY. USE IC697ACC701 ENABLED USE THIS MODULE IN SLOT 1 ONLY RUN WITH OUTPUTS ENABLED RUN WITH OUTPUTS DISABLED STOP Figure 2. CPU 731- Location of Major Features 3 12 MHz, 32 Kbyte Central Processing Unit GFK-0159J PLC CPUs August 1997 Series 90 -70 Programmable Controller Data Sheet Manual GFK-0600F 12-3 Programmer Connection, Parallel For a parallel interface (MS-DOS programmer only) connect the programmer to the top port connector on the Bus Transmitter Module (IC697BEM713) as shown in Figure 1. Consult Reference 2 for a description of programming functions. Serial Port The 15-pin D-connector provides the connection to an RS-485 compatible serial port as shown in Figure 3. This port provides a serial connection to a Standard Serial COM port, or to a Work Station Interface board installed in the programming computer. For more information on serial communications, see references 1, 2, and 3. PS CP U B TM GB C B RM IC66* I/O BUS (7500 FEET MAXIMUM) RACK 7 ONE METER TOTAL LENGTH OF ALL INTERCONNECTION CABLES FROM BTM TO LAST BRM IS 50 FEET (MAXIMUM). ALL RACKS MUST BE AT SAME GROUND POTENTIAL (8 RACKS MAXIMUM). NOTE SERIAL P CM I/O BLOCK or N BC Figure 3. System Configuration, Serial Connection to Programmer Programmer Connection, Ethernet TCP/IP Connecting your programmer via an Ethernet TCP/IP network requires installation of an Ethernet Interface module in the PLC. This can be either the Ethernet Controller, IC697CMM741, or Ethernet Interface (Type 2), IC697CMM742. Before connecting your programmer and PLC to the Ethernet TCP/IP network you must set the IP address in the Ethernet Interface. After setting the IP address, connect the PLC and the programmer running Windows software to the Ethernet Interface. For more detailed information on the programmer connection via Ethernet TCP/IP, refer to the TCP/IP Ethernet Communications (Type 2) User s Manual, and the Windows programming manual, GFK-1295. Configuration The IC697 CPU and I/O system is configured with MS-DOS or Windows based programming software. There are no DIP switches or jumpers used to configure the system. The CPU verifies the actual module and rack configuration at power-up and periodically during operation. The actual configuration must be the same as the programmed configuration. Deviations are reported to the CPU alarm processor function for configured fault response. Consult Reference 1 for a description of configuration functions. Batteries A lithium battery (IC697ACC701) is installed as shown in Figure 2. This battery maintains program and data memory when power is removed and operates the calendar clock. Be sure to install the new battery before removing the old battery. If during power-up diagnostics a low battery is detected the Module OK LED (top) will not stay on. Specific indication of a low battery state is detailed in Reference 2. GFK-0159J 12 MHz, 32 Kbyte Central Processing Unit 4 PLC CPUs August 1997 Series 90 -70 Programmable Controller Data Sheet Manual GFK-0600F 12-4 Removing a Module The following instructions should be followed when removing a module from its slot in a rack. Grasp the board firmly at the top and bottom of the board cover with your thumbs on the front of the cover and your fingers on the plastic clips on the back of the cover. Squeeze the rack clips on the back of the cover with your fingers to disengage the clip from the rack rail and pull the board firmly to remove it from the backplane connector. Slide the board along the card guide and remove it from the rack. Table 1. Specifications for IC697CPU731 Battery Shelf Life 10 years at 20 C (68 F) Memory Retention 6 months nominal without applied power Current required from 5V Bus 1.0 Amp Time of Day Clock (internal timing) Accuracy 3.5 seconds per day Elapsed Time Clock .01% maximum Serial Port RS422/485 compatible, programmer serial attachment VME System designed to support the VME standard C.1 Refer to GFK-0867B, or later for product standards and general specifications. Table 2. References Reference Title 1 Programming Software User s Manual 2 Programmable Controller Reference Manual 3 Programmable Controller Installation Manual Table 3. Ordering Information Description Catalog Number Central processing Unit, 12 MHz, 32 Kbyte, Fixed IC697CPU731 Lithium Battery IC697ACC701 Note: For Conformal Coat option, or Low Temperature Testing option please consult the factory for price and availability. 12 MHz, Expandable Central Processing Unit IC697CPU771 PLC CPUs GFK-0349F August1997 1 13 Series 90 -70 Programmable Controller Data Sheet Manual GFK-0600F 13-1 12 MHz, Expandable Central Processing Unit (IC697CPU771) datasheet GFK-0349F Features Single slot CPU 2K inputs and outputs (any mix) Up to 8K analog I/O 0.4 microseconds per boolean function 12 Mhz, 80C186 microprocessor Supports IC660/IC661 and IC697 PLC Programmed by MS-DOS or Windows based software products running on Windows 95 or Windows NT over Ethernet TCP/IP or through the SNP port. Supports up to 512 Kbytes of battery-backed expansion memory in the same slot Configurable data and program memory Battery-backed calendar clock Three position operation mode switch Password controlled access Three Status LEDs Software Configuration (No DIP switches or jumpers) Reference information inside front door. Functions The CPU 771 is a single slot PLC CPU which is programmed and configured by MS-DOS or Windows based programming software to perform real time control of machines, processes and material handling systems. The CPU 771 CPU communicates with I/O and smart option modules over the rack-mounted backplane (IC697CHS750, 782, 783, 790, 791) by way of the VME C.1 Standard format. Supported option modules include all IC697 LAN interface modules, several Coprocessor modules, Bus Controller for IC660/661 I/O and Communications modules, in addition to all of the IC697 family of discrete and analog I/O modules (see the applicable Programmable Controller Installation Manual for more information on supported modules). Program and data memory is available by the attachment of an expansion memory board with up to 512 Kbytes of battery-backed CMOS RAM.
Give us a call at 1-800-360-6802 or 1-919-535-3180. We can help you with your Revision specific needs.
UPS Ground shipping is always FREE!
These “New Surplus” units are a great cost saving alternative. This product is in the original manufacturer’s packaging with all sub-assemblies and documentation. Comes with a PDF Electric & Supply 3-year warranty.
UPS Ground shipping is always FREE!
Surplus New - New unused and includes all sub-assemblies and documentation. Product may ship in manufacturer or PDF Electric & Supply packaging and includes a PDF Electric & Supply 3 Year Warranty.
UPS Ground shipping is always FREE!
Reconditioned products from PDF Electric & Supply are a cost-effective alternative to new and obsoleted PLC products. Every part is reconditioned down to the circuit board level. All parts are thoroughly inspected and hand-cleaned before being functionally tested in a fully configured system.
Our Reconditioned Products always come with a PDF Electric & Supply 2-Year Warranty.
UPS Ground shipping is always FREE!
3-5 Days for most repairs. 24 hour repair upon request at no extra charge. If part is unrepairable, we will exchange with a working unit or return unrepaired.